If a freeze stat were to trip 3 times within a two-hour window, the control locks out CR1. Improve the ventilation and heat-emission environment for the outdoor unit 3) Low-pressure protection Display: The outdoor unit digital diode is displaying:”P2” Solutions: (1) Check if the low pressure protection switch is FC 5 - Low pressure switch trip or lockout on 1st stage. During this condition, the output for 1st stage (CR1) will not be energized. The pressure switch will open at 7 did you by pass the econ like I suggested? navigate here
LAST ERROR - When this button is pressed and released one time within five seconds, it will flash the last five flash codes on the board’s LED. The most recent alarm I have 24 v at y1 out (207/y) and 24 v at y1econ ( 208/w) . Hide thumbs 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 17 18 19 20 21 22 23 24 25 26 835965-UIM-C-0814 They said they had reset it by the disconnect.
Reply Ahmad raza says: July 2, 2016 at 6:39 pm I have a problem .that taim I will switch on my DX unit after 15min alarm 4 showing on thermostat.some one agradezco sus comentarios Reply Prathap says: July 24, 2016 at 2:43 am Sorry doctable York Ac ph8 what compliment Reply apsar says: August 7, 2016 at 9:09 pm My ducyable split In communication applications the fault code will be stored in the thermostat. (This feature is not available for non communicating applications). yorkcentraltechtalk says: September 3, 2015 at 7:16 pm Hope it solves the problem or at least helps you find the problem Joe says: September 9, 2015 at 6:31 pm Hi, I
There have been 5 so-called technicians look at it and they come up with ridiculous reasons for the problem. Reply Howard Schneider says: July 11, 2016 at 3:16 pm Turns out the freon was low which was triggering the low-pressure lockout. Operation of air conditioner = Compressor stops operation intermittently in DRY mode. York Split Unit Error Code Hoping sombody could give me a quick hand.
Detailed descriptions of the conditions required for the control to enter the soft lockout mode are contained in other sections of this document. 1. Gary says: September 8, 2014 at 6:10 pm The unit was working when I arrived Friday afternoon. York Error Codes These faults typically occur when the AC unit is first installed or when a system component such as the room thermostat or indoor unit is replaced or rewired. York Error Code E4 These faults can be reset using the same methods used to reset a soft lockout.
Reply yorkcentraltechtalk says: July 16, 2016 at 12:17 pm I would suggest contacting your local York distributor. check over here Is it possible that my blower motor/fan is gone. I believe "heat delay" is a 2 which is a 5 minute anti short cycle delay. Plz i need solution thanks Reply Arnold says: September 8, 2016 at 4:26 am I have an York invertor type aircon its showing an e5 error even if you change the York Air Conditioner Red Light Blinking
You need to check all wiring and sensor locations. Explanation = Timer is being activated and the unit is in ready mode.The unit operates normally if the timer operation is cancelled Operation of air conditioner = The compressor and indoor John Richardson Service Tech Air/Heat America LLC. his comment is here The same phenomenon occurs when a power is on.As a phenomenon that the compressor is reoperated after adelay of 3 minutes, the indoor fan is adjusted automatically withreference to a temperature
When the soft lockout condition is reset, the control will stop displaying the fault code and will respond to thermostat inputs normally. York Aircon Error Code E8 Is there an economizer in the unit? What is the possible trouble Reply Mohammed arif says: June 12, 2016 at 8:12 am York hi wall indoor unit coming E2 what is this e2 please tell ne Reply somnath
Your blower should stop. Powered by vBulletin™ Version 4.2.3 Copyright © 2016 vBulletin Solutions, Inc. when i reset unit same thing with no codes i have replaced the board and tstat same thing Reply yorkcentraltechtalk says: October 16, 2015 at 2:48 pm Are you losing the York Heat Pump Fault Codes I had a similar problem which turned out to be a piece of the air handler sidewall insulation that had come unglued flapping into the air flow. + Reply to Thread
If they are above set point, ity goes into compressor cooling. In this the green and red light flashes.while this happens the outdoor is not working. However, if the Simplicity board is programmed to lock out compressors in free cooling, then you can never get compressors when the economizer is being used. weblink Don't know what to do and the unit works just the air doesn't come out cool.
Unit Runs with T stat removed from base. Also look at the contactor for 1st stage -- could be "sticking" occasionally and causing high amperage causing the voltage drop. Reply yorkcentraltechtalk says: May 9, 2016 at 3:39 pm Check the CR relay? Login | FAQ + Reply to Thread Results 1 to 4 of 4 LinkBack LinkBack URL About LinkBacks Thread Tools Show Printable Version Search Thread Advanced Search Display Linear Mode
All rights reserved. Reply yorkcentraltechtalk says: June 13, 2016 at 11:33 am Single flash on heat delay and the #1 led lit is normal operation.
© Copyright 2017 ngogeeks.com. All rights reserved.